Organic Rankine Cycle
Waste Heat to Power ORC search was updated real-time via Filemaker on:Waste Heat to Power ORC | Return to Search List
Search Completed | Title | CHAPTER 4 THERMODYNAMIC ANALYSIS OF SUPERCRITICAL RANKINE CYCLE
Original File Name Searched: 13_chapter_4.pdf | Google It | Yahoo | Bing
Text | CHAPTER 4 THERMODYNAMIC ANALYSIS OF SUPERCRITICAL RANKINE CYCLE | 001
THERMODYNAMIC ANALYSIS OF SUPERCRITICAL RANKINE CYCLE
The computer program which was developed by the present investigation as presented in Chapter 3 has been used to find different steam properties at different operating conditions of pressure and temperature and thermodynamic analysis of the cycle has been presented in this chapter. In section 1.2, the basic cycle of operation of steam power plant based on the Rankine cycle has been presented. To carryout thermodynamic analysis of this cycle the assumptions and range of variable parameters are given below.
4.1 ASSUMPTIONS MADE IN THE ANALYSIS
i. Capacity of the power plant = 1000 MW
ii. The isentropic efficiency of the steam turbine is 90%.
iii. The pump efficiency is assumed to be 85%.
iv. Cooling water temperature inlet to the condenser Twi=250C
v. Terminal Temperature Difference (TTD) = 50C
vi. Heat and pressure losses in the transport pipe in between the
different units of the cycle are negligible.
Image | CHAPTER 4 THERMODYNAMIC ANALYSIS OF SUPERCRITICAL RANKINE CYCLE
|Waste Heat to Power - ORC - - Waste Heat to Power System - Go to website|
Search Engine Contact: email@example.com